Combined hot water tank
Druzstevni zavody Drazice strojirna s.r.o.
Operating position horizontal
The combined storage water heater with horizontal operating position designed for premisses with the lack of space with volumes between 125200 litres. The water heater may be fixed on the wall using the supplied brackets or fitted in horizontal position on adequate construction. It is always necessary to count with the lack of space above and below the water heater for fitting of the supply pipeline.
Electric power. Ceramic heating element controlled by the operating thermostat and secured by the safety thermostat (thermal fuse).The thermal range is 574 °C. Connection voltage is 1-PE-N/AC 230 V/50 Hz.
Exchanger. The water heater may be connected to an external hot water source with the max. temperature of 110 °C and pressure of 0.4 MPa . Heating is assured by a high performance two-shell exchanger by layers of hot water. The exchanger warms water in the upper part of the vessel and then in the lower layers of the vessel. This method of continuous heating is appropriate for self-circulation central heating systems and small self-circulation solar systems.The heat exchanger works both in forced circulation mode and in self-circulation system. The heating water regulation sensor may be inserted into the common receiver with electric installation sensors.